Experimental Physics and
Do you mean I should uncomment this line: in "CH\$1:SCA?"; ?
ReplyTimeout = 5000;
out 'CH\$1:SCA %g';
in ":CH\$1:SCALE %g";
This won't work because when the probe_ch1 is processed it causes CHx_Voltage ($(P)$(R)setY1) to process, the latter will send the command to set the current vertical resolution - so it will first set the current value, then will read the current value, not the new value. You see - I have to either use open_loop or closed_loop, not both at the same time. Or I could add another readback record, but this will mess up the HMI with another widget.
On Mon, Jun 4, 2012 at 3:31 PM, Mark Rivers <firstname.lastname@example.org> wrote:
I would suggest having CHx_Voltage read the current vertical resolution. Leave this record Passive. But have the probe_ch1 record's FLNK be CHx_Voltage, so it reads the vertical scale once each time you change the probe attenuator.
Pavel Maslov, MS
Controls Engineer at Pulsed power Lab
Efremov Institute for Electro-Physical Apparatus
St. Petersburg, Russia
Mobile: +7 (951) 672 22 19
Landline: +7 (812) 461 01 01
|ANJ, 18 Nov 2013||
· Search · EPICS V4 · IRMIS · Talk · Bugs · Documents · Links · Licensing ·